|Electronics Forum||Help Search Members Calendar|
|Welcome Guest ( Log In | Register )||Resend Validation Email|
Posted: September 21, 2010 01:55 pm
Member No.: 28,874
Joined: March 29, 2010
the relay will switch between my inverter i have running on batteries and the wind turbine and then when/if the batteries get too low and the inverter turns off from low voltage, the relay will change back to the mains power so i dont have to live in the dark while waiting for the wind to pick up.
question is, can anyone suggest a good relay to do the job? i have 9 lights in my house; 1 fluro tube and 8 regular fluro lights that they replaced incandescents with.
most of them are 11watt.
i have a 150watt square wave inverter that should be able to handle the job no problem.
i was thinking of this relay here, what do u guys think?
Posted: September 21, 2010 02:08 pm
Forum Addict ++
Group: Spamminator Taskforce
Member No.: 792
Joined: April 25, 2004
The relay has a 12VDC coil.
The mains should be holding the relay, not the inverter.
Get a small C/O contactor with an auxiliary contact for activating the inverter.
Posted: September 21, 2010 07:58 pm
Forum Addict ++
Member No.: 5,746
Joined: July 24, 2006
Not if the inverter is meant to be the primary power source.
The scheme should work, & you need to size the relay to the current capacity of your mains fuse/breaker.
If this is meant to be a plug in device, then include a fuse & size it & the relay to your desired load capacity. Include a generous safety factor.
For 150W inverter capacity, I would use a 2 amp fuse, & a 5 amp or larger relay. Larger relays would tend to last longer in this application.
Trouble rather the tiger in his lair, than the sage among his books.
For to you, kings & armies are things mighty & enduring.
To him, mere toys of the moment, to be overturned at the flick of a finger.
Fortuna favet fortibus.
:: support us ::